- Q. We are a ready-mixed producer in northern Wisconsin. Several contractors we supply have placed in-floor heating in garage or basement floors. Two of these floors have cracked after turning on the heat. We have been told that this may be due to thermal cracking or shocking. We would like information to pass along to contractors the proper procedures for installing these tubes. How and when should homeowners begin using the heat?
A. If cold weather had already set in and the slab was thoroughly chilled or frozen, then suddenly turning on the heat could lead to thermal cracking. Barring that, turning on the heat may have just accelerated the drying process and the cracks you mention may have occurred eventually even without the in-floor heat.
The specific crack pattern might give some clues to whether it was normal shrinkage cracking or thermally induced. To avoid problems during future cold-weather start-ups, the slab temperature should be raised gradually over a period of several days.
You don’t say whether these were electric or hydronic installations, but in either case, radiant heating systems only raise the floor temperature into the 80º F range. Attention to details is important in these systems. For example, in-floor installations should have insulation below and around the edges of the slab.
The Radiant Panel Association (www.radiantpanelassociation.org